FiberTEK III Series
- Attenuation/insertion loss (dB) measurement
- Multimode and single-mode options
- Encircled Flux compliant (optional)
- Built-in visible light source for troubleshooting
- Full Tier 1 fiber certification
- Complies with TIA/ISO/IEC
$5,905 - $10,765 MSRP
FiberTEK III adapters are used with LanTEK III for fast and simple certification of high bandwidth single-mode and multimode fiber optic cabling including support for encircled flux testing (optional).
To pinpoint fiber cabling faults every FiberTEK III adapter includes a built-in visible light source to help you visually pinpoint faults and locate fiber ports.
FiberTEK III provides optical loss (dB) measurements meeting Tier 1 certification requirements.
Available in multi-mode (850/1300nm) and single mode (1310/1550nm) varieties.
Click here to view the LanTEK III cable certifier.
Click here for the TREND AnyWARE app.
Tier 1 certification results display:
- ISO/TIA/IEEE test standard
- Pass/Fail result
- dB loss of each fiber at each wavelength
- dB loss in each direction (when testing bi-directionally)
- Fiber link length
- dB margin / headroom
FIBERTEK III-MM LED KIT
R164005 - FiberTEK® III multimode (850/1300nm) kit with LED light sources for standard multimode fibre.
FIBERTEK III-SM LASER KIT
R164006 - FiberTEK III single mode (1310/1550nm) kit with laser light sources for single mode fibre.
FIBERTEK III-MM LED & SM LASER KIT
R164007 - FiberTEK III combination MM/SM kit with LED MM sources and laser SM sources.
FT III/IV - Encircled Flux 50/125µm cable SC - SC
R164050 - FT III/IV-Encircled Flux 50/125um Cable SC - SC. Compatible with FiberTEK III and FiberTEK IV.
FT III-Cable Kit SC/PC MM 50/125um
R164053 - FT III-Cable Kit SC/PC MM 50/125um
FT III-Cable Kit FC/PC MM 50/125um
R164054 - FT III-Cable Kit FC/PC MM 50/125um
FT III-Cable Kit ST/PC MM 50/125um
R164055 - FT III-Cable Kit ST/PC MM 50/125um
FT III-LC 50/125um F/Optic Cables and Couplers
R164056 - FT III-LC 50/125um F/Optic Cables and Couplers
FT III-Cable Kit SC/PC SM 9/125um
R164057 - FT III-Cable Kit SC/PC SM 9/125um
FT III-Cable Kit FC/PC SM 9/125um
R164058 - FT III-Cable Kit FC/PC SM 9/125um
FT III-LC 9/125um F/Optic Cables and Couplers
R164059 - FT III-LC 9/125um F/Optic Cables and Couplers
FT III/IV-Set of SC FC PC and ST Screw on Adaptors
R164060 - Screw on adapters for FiberTEK III/IV.
FT III-Cable and adapter kit LC MM 50/125Âµm
R164061 - FT III-Cable and adapter kit LC MM 50/125Âµm
FT III-Cable and adapter kit LC SM 9/125Âµm
R164062 - FT III-Cable and adapter kit LC SM 9/125Âµm
FT III-Carrying Case (Single)
R164063 - FT III-Carrying Case (Single)
FT III/IV-LC Receiver Adapter (Single)
R164064 - FT III/IV-LC Receiver Adapter (Single)
One-Click Fiber Cleaner STC-FC-1.25mm
33-963-11 - This 1.25mm One-click Cleaner is a high-performance and easy-to-use fiber tool that has been designed to clean both the
One-Click Fiber Cleaner STC-FC2.5mm
33-963-10 - This 2.5mm One-click Cleaner is a high-performance and easy-to-use fiber tool that has been designed to clean both the m
Sapphire Care Plan - Fiber (Per Pair) - 1 Year
SCP1YF - Sapphire Care Plan for FiberTEK III and FiberTEK IV adapters - 1 Year - Applicable within Europe and the USA. Include
Sapphire Care Plan - Fiber (Per Pair) - 2 Years
SCP2YF - Sapphire Care Plan for FiberTEK III and FiberTEK IV adapters - 2 Years - Applicable within Europe and the USA. Includ
Sapphire Care Plan 3 Years - 10% Discount
SCP3YRN - (3 year - 10% discount included when purchased within 60 days of purchasing a new LanTEK III/IV)
FT III/IV-Encircled Flux 50/125um Cable SC - LC
R164051 - FT III/IV-Encircled Flux 50/125um Cable SC - LC
Download and view the latest manuals, quick reference guides, firmware and software updates, and approvals. Registration is required.
Frequently Asked Questions
- Q: What is the difference between single-mode and multimode fibre?A: Multimode fiber has a larger light carrying core of 50 or 62.5 microns compared to 9 microns for single-mode fiber. The larger core of multimode fiber captures more light than single-mode fiber allowing the use of low power LED light sources. The maximum bandwidth of multimode fiber is inversely proportional to length, i.e., doubling the length of a multimode cable reduces it’s bandwidth capacity by half. Multimode fiber is typically limited to lengths of 2,000 meters (6,560 ft). Single-mode fiber requires the use of higher power and more costly laser light sources but does not sacrifice bandwidth for distance. Single-mode fiber can be used at lengths of up to 40,000 meters (131,200 ft) while supporting 10 Gb/s data rates.
- Q: Which LanTEK III models support fibre testing ?A: Both LanTEK III-500 and LanTEK III-1000 support FiberTEK III
- Q: Will LanTEK II support FiberTEK IIIA: Yes
- Q: Will LanTEK III support FiberTEK II ?A: No
- Q: Can I measure MPO connectors with FiberTEK IIIA: Not directly. Due to the still not very high repeatability when disconnecting and connecting MPO connectors, TREND still recommends to use so called fan-out cables from MPO to SC or LC
- Q: Can I measure LC links with FiberTEK IIIA: Yes, there are optional adapters available
- Q: Which products from Trend Networks test Tier-1 / Tier-2 ?A: FiberTEK III and FiberTEK IV test Tier-1. The OTDR II tests Tier-2.
- Q: Do you need to do both Tier 1 (OLTS testing) and Tier 2 (OTDR testing) to complete a Tier 2 certification ?A: Tier-2 certification is a supplement to Tier-1 certification meaning both an attenuation measurement with a power meter/light source (OLTS) and an OTDR measurement are required. It is for this reason many OTDRs have options for an integrated power meter. With the power meter built in to the OTDR, both measurements can be stored on a single instrument to simply reporting.
- Q: When testing 2 fibres with an OLTS, can the fibres be looped at the far end so one person can test both fibres with a single tester or does each fibre need to me measured individually?A: Looping the fiber is not a recognized method of OLTS testing because if the loss is too high you cannot know which fiber has a problem. When someone has an OTDR w/power meter the assumption is a stand-alone light source will be used at the opposite end of the cable to test each fiber individually. Having the OTDR w/ power meter is more convenient because the results for both Tier 1 and 2 tests can be stored on the same piece of test equipment.
- Q: Is bi-directional testing required for OLTS & OTDR testing ?A: Standards do not require bi-directional testing. For multimode fibre they require testing at 1 wavelength. 2 wavelength testing is optional. For single-mode fiber 2 wavelength testing is highly recommended for two reasons: First – single-mode cables can be long enough that the total attenuation can be very different at each wavelength because attenuation from bends in the cable depend on the wavelength. Second and more importantly - 2 wavelength testing can identify a bend vs a splice. Attenuation for a bend is different depending on the wavelength, but attenuation from a splice should be very similar at both wavelengths. The OTDR software assumes an event with similar loss at both wavelengths is a splice and an event with different loss values is a bend. This is the only way it can correctly identify a splice vs a bend. Bi-directional testing is useful for identifying mismatched fiber types. The loss with an OLTS or OTDR should be the same in each direction. However, if different types of fiber are connected together such as 50 & 62.5um multimode or single-mode fiber with different NA values (numerical aperture) the loss will be different in one direction vs the other. With an OLTS you see only the total loss, but a difference in measurements indicates there is a mismatch of sorts. An OTDR will show the location of the mismatch. A splice measured in one direction may show +0.5dB (gain) and in the other direction may show -0.3dB. When added together the result is -0.2dB which is the actual value of the splice. Standards do not require bi-directional testing. It is purely optional and used to identify issues like those mentioned above.
- Q: Does Tier-1 testing require polarity and length measurements ?A: There is no requirement to identify the polarity of the fibers, but this is a good reason for bi-directional testing. If the fibers are tested in both directions polarity does not matter. The cables are supposed to be installed so that the TX/RX is reversed but this is a documentation issue more than testing. The requirement to measure length depends on the standard being tested. TIA/ISO limit the length for horizontal fiber runs to 90m just like copper cable, so it is required to test length. TIA/ISO also have specifications for cable attenuation per km. For example multimode 850 must be 3.5dB/km or less - this is for the fiber only, not including connectors. Obviously to perform the calculation the cable length must be measured. This is difficult with an OLTS because it does not know how many connectors are in the link and are affecting the total loss. Practically speaking, an OTDR is the only way to do this measurement accurately. Some application standards like IEEE 10GBase-SX (10Gbps @ 850nm) only have a specification for maximum loss, not length. So as long as the loss is under the limit, cable length does not matter. There are big differences when testing TIA/ISO vs IEEE. TIA/ISO standards are written without reference to a specific application and are intended to provide installation guidelines for a generic cabling system that supports many different applications. IEEE test limits apply to each application and allow a user to ensure that a specific application will run on the cabling being tested. Cabling installers rarely know what application the network owners plan to use which is why installers test to TIA/ISO generic cabling standards. Most IEEE standards specify minimum cable distances for multimode fiber for the different grades: OM2, OM3, OM4 and OM5. This only means the bandwidth specified by the fiber grade is available to at least the minimum distance. It is not a distance limit and the bandwidth may be available at further distances for fiber that exceeds the minimum bandwidth ratings.